FedEx and UPS are notifying us of possible delivery delays today due to winter weather last night at their Memphis and Louisville hubs, respectively. Please visit FedEx Service Alerts and UPS Service Updates for more information.
AutomationDirect will close at 3:00 PM ET on Wednesday, Nov 21st. We will also be closed on Thursday & Friday, Nov 22nd & 23rd, for Thanksgiving. The shipping cutoff for same-day FedEx shipments on Wednesday, Nov 21st is 3:00PM ET. Freight shipments as well as customer pickups deadline is 1:00PM ET. There will be NO UPS shipping available on Wednesday. Orders placed after the same-day shipping cutoff times will ship on Monday, November 26th.
Need help selecting a PLC family? Use our selection tool to configure and order.
The PLC base unit provides a means of housing and connecting the installed I/O. Modular base units have slots for interchangeable I/O connections to the backplane's data bus. DirectLOGIC 205 PLC bases come with 110-220VAC, 12-24VDC or 125VDC power supply options and various slot configurations.
DL205 PLC Expansion Modules The D2-260 and D2-250-1
support local expansion. The D2-260 supports local expansion up to
five total bases (one CPU plus four expansion bases) and the
D2-250-1 supports local expansion up to three total bases (one CPU
bases plus two expansion bases). Following are the modules
required for expansion:
D2-CM - The D2-CM expansion base controller module
is placed in the CPU slot of each expansion base. The module
includes a rotary switch for selecting the expansion base number,
as well as PWR, RUN and DIAG LEDs for system status indication.
D2-EM - The D2-EM expansion module attaches to the
right side of each base in the expansion system. It comes with
two RJ-45 cable ports for expansion cables to plug into, a single
ACTIVE LED for system status indication, and a TERM toggle switch
for last and first base termination.