|AutomationDirect Live Chat|
Check out the list of all tutorial videos on the C-More Micro HMI at this link:
You can calibrate the touch screen from the Panel’s Setup Menu. Hold down the F1 and F5 keys at the same time for 3 seconds and the setup menu will come up. Unfortunately, we can’t do that here in the simulator BUT we CAN simulate pressing both function keys down by right clicking and selecting Setup Menu. From here you click on “Setting” - “Calibration” and then just follow the directions. press on this cross mark – so we press on this cross mark, then we press on that cross mark, and we press on this one, F5 to save and quit, F1 to Retry – we’ll save it – and now touch screen is fully calibrated. That’s all there is to calibrating your screen – be sure to check out the other videos in this series. And as always, please send us any topics you would like to see covered – or - any other comments for that matter – we appreciate the feedback!