This video gives basic information on Using the OFFDTMR "Off Delay Timer" instruction in the Do-more Designer software. It presents information that is commonly missed by users. This WILL NOT be a complete tutorial for the instruction but rather a supplement to the help file and customer experience.
Our FREE Practical Guide to Programmable Logic Controllers eBook: https://www.automationdirect.com/ebooks/plc-handbook
This is a multi-scan instruction, because it takes multiple scans to complete, it cannot be used in either Subroutines or Interrupt Service Routines. It can used in Programs and under special circumstances can also be used in Stages inside of a Program or in Tasks. See the help topic “Instruction Set Chart” for more information. This instruction works by this timing chart. Notice you are delaying when the output turns off, but the output turns on as soon as the input becomes true. The input has to turn off before the off delay time will start counting down. Here is an example of using this timerto delay turning off an output by 5 seconds. If you use a variable for the delay make sure to note that this is in milliseconds