The LC52 level controller comes configured for 120VAC. Learn how to convert it to 240VAC operation.
To switch between 120 and 240 Volts AC, just remove the back plate, Pull the circuit boards and switch these two jumpers. With these jumpers set like this the controller is set for 120 VAC power and with the jumpers set like this, the controller is set for 240 VAC operation. Fold the boards back up make sure the LEDs and the switches line up with the holes in the top of the housing, and insert assembly back into the box. The slots the boards fit into only come half way up the housing so keep an eye on those when replacing the electronics. Replace the insert if it fell out, then screw the back on. That’s it! Check out the other videos in this series to learn how to use your Flowline Remote Level Controller, from Automation Direct. And if you need any help, please don’t hesitate to call Automation Directs free, award winning tech support during regular business hours. They will be happy to help you. And check out the forums. There are lots of folks there that love to share their years of experience. But don’t post any questions to tech support there; they don’t monitor the forums on a regular basis.
Voted #1 mid-sized employer in Atlanta
Check out our job openings