- In this video we show the process needed to connect a C-more HMI for remote programming over the StrideLinx VPN Cloud. This connection will allow remote access to HMI and also program the C-more HMI remotely.
You will need a C-more Human Machine Interface with ethernet, the C-more Programming software, and a StrideLinx VPN router that has been configured. If you have not configured your router, please view the video below that corresponds with your version of router.
Initial setup videos:
In this video, we will show the process of getting connected to a C-more HMI through the StrideLinx VPN connection. If you have not already setup you Router please see the videos for the initial setup, in the description below. Once you have setup your router, then continue on to this video. First, we need to discuss the C-more IP address setup. In this example, this is IP address of the VPN router on the control side. To remotely program your C-more HMI it must be on the same subnet as the VPN router and have the IP address of the Router as it’s Default Gateway. This way the C-more will be communicating through the router. It is very important that everything is a static IP address, as one limitation of VPN networks is that Broadcast comms will not work and broadcast comms is what is used for auto discovery of devices. Now let’s set up the C-more’s IP address locally for the first time. So, with your C-more project open, select setup, Panel Network and then select the Ethernet Tab. So, enter in the IP address information we discussed before. And then select ok. And send this project to your HMI Now that the HMI PLC has been setup and shipped to the remote location, let’s make our first connection through the StrideLinx and read our project from the panel.. Open up the StrideLinx page, select your device and then connect. Once the IX client is connected, open up the C-more software and then select Read from Panel. Select Ethernet and then browse. Under Network, select the Windows Tapp Adapter. This is the virtual connection that the IXClient uses to connect to the VPN cloud. Now, select the Remote Link List and then Add. Give this connection a name. Enter in the IP address of the C-more Panel and then typically on remote connection like this I increase the Timeouts to the max. Hit Ok. Now select the link that we just created and select Ok. Now the software will browse for the Panel and then give you a go no/Go, on the Connection. Now select to read the project. Now you can make changes to your project and update the panel. Let’s go one step farther here, and show remotely viewing the the panel with the Remote access feature. In the C-more panel, to turn on remote access in your project. Go to Setup and then Panel Network. To turn on Remote access there is two parts to this. We must turn on the Web server and then activate the Remote access. While we are here if you are emailing alarms, through your HMI, we must allow internet access with the VPN Router. This can be found in the dashboard under configuration. So, under Web server enable this function. You can also change which port this uses and secure the communication with a password. I am going to leave it open for the purposes of this video. Now Select the Remote Access tab. Since this VPN makes you part of the local network we do not need to add the complexity of the remote connection. I am going to leave the permission as View Only and use the default Account name without a password. This setup can be more advanced I just want to show the basic features of this connection. Now select Ok and send this project to your HMI. Once this is loaded, open up an Internet browser and enter in the IP address of this HMI. Now select the remote access Link. And now select the No firewall. This will download an executable file that you can run on your PC. So, select the application and not you will be asked to enter in the user name and password. Select Ok. And now we can view the panel. This connection can make Improving, Controlling and monitoring your HMI and control system much easier. A little safety disclaimer. Before you make any changes to your PLC Remotely take into account what you are activating and deactivating remotely as it may cause an unsafe condition. It is always best to have local eyes on the equipment while making these changes. This is where the digital input on the VPN router can be useful, it will allow you to lock out remote changes until someone is there to monitor to safety purposes If you have any questions about the Stride VPN router please contact AutomationDirect’s support team during regular business hours. They will be glad to help. Click on this video to learn more about AutomationDirect’s many support options, click here to learn more or see more videos about our many products, and be sure to click here to subscribe to our YouTube channel for upcoming videos.
Voted #1 mid-sized employer in Atlanta
Check out our job openings