Cookies are not enabled on your browser.
Cookies are required for our site. Please enable cookies in your browser preferences to continue.
AutomationDirect will close at 3:00 PM ET on Wednesday, Nov 27th. We will also be closed on Thursday & Friday, Nov 28th & 29th, for Thanksgiving. The shipping cutoff for same-day FedEx shipments on Wednesday, Nov 27th is 3:00PM ET. Freight shipments as well as customer pickups deadline is 1:00PM ET. There will be NO UPS shipping available on Wednesday. Orders placed after the same-day shipping cutoff times will ship on Monday, December 2nd.
(VID-DD-0025) - This video gives basic information on Using the UDC "UP Down Counter" instruction in the Do-more Designer software. It presents information that is commonly missed by users. This WILL NOT be a complete tutorial for the instruction but rather a supplement to the help file and customer experience.
** Software Version used in this video: Do-more Designer 2.0
This is a multi-scan instruction, and because it takes multiple scans to complete, it cannot be used in either Subroutines or Interrupt Service Routines. It can used in Programs and under special circumstances can also be used in Stages inside of a Program or in Tasks. See the help topic “Instruction Set Chart” for more information. This counter has 3 input rungs. One for both UP and One for down and down input. Both of these are edge triggered. This is indicated by the arrow on the input leg. The third input would be the Reset rung. When the reset is true, the counter will reset to zero. Notice that this counter has two preset one for up count and one for down count. When the count is equal or greater that the up preset, the .done bit will turn on. When the count is equal to or less than the down preset, the down DONE bit will turn on.