This version of Internet Explorer is either no longer supported by Microsoft, or is obsolete and some features of our store may no longer be supported.
Please consider upgrading or use a different browser.
(VID-DD-0011) - This video gives basic information on Using the CNT ""Up counter" instruction in the Do-more designer software. It presents information that is commonly missed by users. This WILL NOT be a complete tutorial for the instruction but rather a supplement to the help file and customer experience.
**Prices were valid at the time the video was released and are subject to change.
** Software Version used in this video: Do-more Designer 2.0
This is a multi-scan instruction, because it takes multiple scans to complete, it cannot be used in either Subroutines or Interrupt Service Routines. It can used in Programs and under special circumstances can also be used in Stages inside of a Program or in Tasks. See the help topic “Instruction Set Chart” for more information. The instruction has two power rail connections. One for the up count and one for the reset. Notice that the Up input is edge triggered. When the count is equal or greater than the preset the Done bit will turn on. When this reset rung is turned on the accumulated count will be set to zero. If the reset rung is true the counter will not count.